Fiberglass Pool SpaSuction Main Drain made by CMP 25215-000-000
- Face Diameter : 6 in.
- Length : 2.5 in.
- Type : Suction, Main Drain
- Style : 2 in. Slip
- Color : White
- Material : Plastic
175 GPM Fiberglass Pool suction VGB-2008 Compliant.
WARNING: When using two or more suction ﬁttings on a common suction line, suctions must be separated by a minimum of 3 ft or they
must be located on two different planes (i.e., one on ﬂoor and one on the wall).
WARNING: Do NOT locate suction outlets on seating areas or on backrests for such seating areas.
The maximum ﬂow rating for this suction ﬁtting is 175 GPM. This suction ﬁtting is designed for installation on side wall or ﬂoor of portable
spas, hot tubs, or pools in conjunction with at least one other suction ﬁtting per pump. DO NOT adapt suction ﬁtting to any pipe size
smaller than ASTM 2 SCH 40 PVC. Suction ﬁtting and fasteners should be observed for damage or tampering before each use. Missing,
broken, or cracked suction ﬁttings shall be replaced before use. Loose suction ﬁttings shall be reattached or replaced before use. Mount
suction ﬁttings on the walls, in the foot wells of portable spas,,hot tubs, or pools. Do not mount directly under seats. Follow all winterizing
instructions and recommendations of your pool and spa professional. Open area of the suction cover is 12.88 sq. in.
- Using hole saw, cut/drill the installation hole.
- If optional gasket is used, gasket must be placed How (GPM) around threads of suction wall ﬁtting at this time.
- Place threads of wall ﬁtting through hole from the inside (water side) of tub/pool.
- Install nut from dry side of tub onto the threads of
the wall ﬁtting.
- Using torque wrench, torque nut to <44.0 ft. lbs.
- Verify that the suction cover is properly tightened and secured with stainless steel screw.
NOTE: If silicone is used on ﬁtting, verify that silicone is
compatible with ABS and PVC plastics.
CAUTION: DO NOT over-torque ﬁtting. Excessive torque
can cause premature failure of threads or damage to suction
ﬁtting increasing risk of entrapment.
NOTE: In the event that one suction outlet is completely blocked, the remaining suction out|et(s) serving that system MUST have a ﬂow
rating capable of the full ﬂow of the pump(s) for the speciﬁc suction system.
NOTE: Increasing size of the pump may increase ﬂow rate of suction beyond rated safety limits causing entrapment or death.
CAUTION: Hair or body parts blocking the spa or pool suctions may become trapped and held against the suction ﬁtting. Entrapment
against the suction ﬁttings can result in drowning or other severe injury. Never sit on or lean up against suction ﬁttings. Never exceed
the maximum allowable ﬂow rate stated on the suction ﬁtting. The suction ﬁtting and fasteners should be inspected for damage or
tampering before each use of the facility. Missing, broken, or cracked suction ﬁttings shall be replaced before using this facility. Loose
suction ﬁttings shall be reattached or replaced before use of this facility.